1. Remove the sealing caps from the ends of the MC4 connectors in the CEP(s).
2. For the SOLAR-AE6 kit, connect the positive and negative connectors from one string of solar panels to the CEP. Connect the second string of solar panels to the second CEP. (See Figure 5-E).
3. For the SOLAR-AE4 kit, connect the positive and negative connectors to the CEP. (See Figure 5-F).
4. Recall from the planning section that it may be necessary to use the provided 3’ or 10’ solar extension cables for this step.